Online connection to Climatix IC devices required to read the Alarm ID.
Create a text concept for alarm types to ensure easy assignments in Rule Editor.
The Alarm type view is open.
The Alarm type dialog box opens.
In the Alarm ID field, enter the ID number of the corresponding alarm.
A corresponding alarm must be triggered on the device (e.g. supply air fan fault) in order to enter Alarm ID. INFO: A new alarm type is created the first time an alarm is triggered; Climatix IC fills out the type using available information. Automatically generated alarm types must be modified.
Alarm ID is always the same within an application type (e.g.: AHU1) and does not need to be regenerated each time. INFO: Another Alarm ID is, however, generated on the same functions (e.g. supply air fan fault), but for a different application type (e.g. AHU2).
Enter a description in the Alarm description field. The description is issued as the alarm text.
Enter a label name in the Alarm label field. The label name is used in Rule Editor as the property Alarm types on incoming alarms.
The alarm type is saved and can be used in Rule Editor.