On-event addressing is a rapid configuration approach working together with Siemens ClimatixTM controllers.
The sensor is wired and connected to the Climatix TM controller via Modbus.
Enter addressing mode and configuration workflow via push button
Press the push button for
Press and hold the button
Release the button
Entering the addressing mode, LED is constant orange.
Communication is established.
After a successful pairing, the LED flashes green (1 s on / 5 s off). Otherwise the LED turns back to its original state.
< 10 min
Constant orange in addressing mode
Press once and release the button
If the LED is constant orange, a short press of the push button stops and exits the on-event addressing mode.
After exiting addressing mode, the LED turns back to its original state.
1) The master cannot change the Modbus address (register 764) to 246.
2) The interval between every configuration command for register 764…768 from ClimatixTM is not more than 30 s. If it exceeds 30 s, the addressing mode ends automatically.
3) 10-minute countdown starts from entering addressing mode.