Use the procedure in this section to modify the IP network settings for an PXC.A device.
BACnet/SC configuration is done entirely in the ABT Site tool.
- Select Configuration > Network.
- Use the following table to make selections for each item.
- Click Apply changes.
- The new settings are applied and saved. The device may reboot depending on the settings modified.
DHCP - use dynamic IP addressing.
Manual - use a fixed IP address. Complete the IPv4, Subnet mask and Router fields.
(Information only) MAC address of the device.
Preferred DNS server.
Device name on IP
Allows you to change the device name online.
Enabled – SNMP monitoring is active.
Disabled - SNMP monitoring is not active.
SNMP read community
Community string that allows reading information from a device.
UDP port grp comm.
UDP port number that the service uses to communicate. Range is 0 to 65535. Default: 47808 (BAC0)