Number of integration data points
up to 500
Number of digital inputs for potential-free contacts for signaling functions NO or NC (onboard)
Number of BACnet/MSTP devices per RS485 interface
up to 60 2)
Number of BACnet/SC devices as a BACnet/SC hub
up to 100
Number of KNX PL-Link devices
up to 64
Number of configurable RS485 interfaces either for integration of Modbus RTU or BACnet MS/TP
1) For details on engineering, see PXC4, PXC5 & PXC7 Planning overview, A6V13054435.
2) Depending on the behavior of the third-party MS/TP devices.