The temperature switching differential can be controlled by PID algorithm and “2-position”. You can check the option under “Advanced Settings”> “Optimization”> “Heating control loop”.
The differential is controlled by PID algorithm based on heating request.
The differential is controlled by “2-position”. The hysteresis value is 0.5 °C. When the room temperature is 0.5 °C above the setpoint, the thermostat stops heating. When the room temperature is 0.5 °C below the setpoint, the thermostat starts heating.
The temperature switching differential work cannot be directly influenced by the user.