The room automation stations can be snapped onto standard rails or screwed onto a flat surface.
Risk of overheating for failure to comply with ambient temperature
Burning and damage to the device
- Ensure sufficient ventilation to comply with the permissible ambient temperature within the panel or installation box. The temperature must be at least 10 K (18° F) lower outside the installation box.
Ambient temperature -5...45 °C (23...113°F)
Ambient temperature -5...50 °C (23...122°F)
Differential pressure sensor
- Avoid bends and pressure when attaching the tube.
- Connect the "+" connection on the side with the higher pressure and the "-" connection on the side with the lower pressure.
- A tube length of 2 m (6 ft) is recommended.