The network address for a full-scale KNX network consists of the area, line and device address. It reflects the exact position of a bus device in the overall network and is unique within the network.
Syntax of the network address
Range 0: Ex works for Synco bus devices = 0 (backbone)
Line 1...15: Ex works for Synco bus devices = 2
Device 1...255: Ex works for Synco bus devices = 255
Excepting OZW775 central communication unit = 150
Area and line address
The Synco bus devices are factory-set with the KNX-defined area and line address 0.2.
The "individual address" (a term from the KNX world) consists of the address components area, line and device, and corresponds to the network address already defined.
The "physical address" is another term for "individual address".
In KNX terms, a subnetwork is the same as a line. Hence, the subnetwork address consists of the address components "area" and "line".